EQJW Heating controller with digital user interface. Heating controller with communication capability for weather-compensating supply-temperature con-. Find out all of the information about the Fr. Sauter AG product: heating controller EQJW Contact a supplier or the parent company directly to get a quote or. View and Download Sauter Equitherm EQJW user manual online. Equitherm EQJW Temperature Controller pdf manual download.
|Published (Last):||1 April 2009|
|PDF File Size:||8.28 Mb|
|ePub File Size:||6.6 Mb|
|Price:||Free* [*Free Regsitration Required]|
The recommended values have been tried and tested but they are not necessarily the ideal solutions for every plant.
Heating controller – EQJW – Fr. Sauter AG
Display of setpoint temperature; flashing: List Of Communication Parameters Index Of Key Words Entering A Switching Command No guarantee is given of the availability and correctness of these numbers. Push the input knob; the time for the switching command is confirmed.
Modbus Bus Wiring Weekly Switching Programme Setting The Date Modbus Data Points holding Register Ending Manual Mode Key To The Operating Instructions Changing Communication Parameters Normal mode corresponds to nominal mode as per EN Table Of Contents Calendar Switching Programme Access To Manual Mode Front View Of The Eqjw Page of 44 Go.
Overview Of Technical Data If CP 12 is set to 1, this controller sends its current flow temperature TF setpoint on the device bus.
Modbus Communication modem with compression and error correction functions, digital telephone network. Table of Contents Add to my manuals Add. Explanations Of Service Parameters Edb Room Operating Eqjs Temporary Esjw Change While the time is running down, the remaining time is shown in days, hours or minutes. Faults Flow temperature sensor: Push the input knob again to confirm the changed numerical value. Viewing Service Parameters Turn the input knob; the value for the parameter is changed Push the input knob; the new value is confirmed Push the ESC button to cancel the procedure.
The anti-frost function is active.
If the room sensor fails, the controller operates according to the settings for operation without a room sensor. An additional modem is used to send alarm texts as SMS to a ewjw telephone, via a provider.
Sauter Components T Table Of Contents Calendar switching programme The value that is entered is added to the measured value for the outdoor temperature. Communication Functions Then, this controller sends its system time to the device bus once every 24 hours.
Overview Of Controller Settings Page 25 – Weekly switching programme Page 26 – Changing and deleting a switching comman An interface similar to an RS is used for this purpose. Setting The Time List Of Service Parameters Press the ESC button once to go directly to the time display.